1055/23 S6 2.4Nm Original New Weishaupt Servo motor Damper actuators For burner
1055/23 S6 2.4Nm Original New Weishaupt Servo motor Damper actuators For burner. Production factory: Bauser GmbH & Co KG. Product name: throttle actuator, servo motor.
Power: 230 v, 50 hz. Travel time: 2.3 s. Apply to the following weishaupt weishaupt burner. L1Z, L3Z, L5Z L7Z L8Z, L8Z / 2, L9Z, L10Z, L11Z, L30Z.
M1Z, M3Z M5Z, MS7Z MS8Z, MS8Z / 2, MS9Z, MS10Z, MS11Z, MS30Z. There are two pieces of air inlets, baffle. The two pieces of baffle are connected by a connecting rod, so that the servo motor can parallel drive.
In equipment commissioning and acceptance, must make the following mechanical adjustment. By adjusting the CAM switch II (partial load of the servo motor), dispatch air damper to part load operation (using the nozzle I work). By adjusting the CAM switch III (capacity) of servo motor, switch to a run at full capacity air damper (with two nozzle work).
2 - will switch to the on solenoid valves. 1 - with the CAM switch electromagnetic valve (2) through the following method to complete this process, after adjusting moving around two-thirds, switch is no longer under pressure. Due to large air flow, this will prevent the flame is extinguished.
After the flue gas measurement, the CAM switch finally adjusted to within the servo motor full load switch (III) and partial load switch II. The function of the type 1055 servo device. Type burner of program-controlled switches. When the terminal closed between 4 and 5 boiler regulator, the programmable device on the terminals 6 of electricity. Terminal voltage on the 11 through "closed" switch IV to LAL terminal 8.
After a short delay, throttle damper under the voltage of the terminal 9 open to full load switch III switch points, and return to burner program controller terminal 8 a interlocking signal. After purging, terminal 9 electricity. By making the terminal 10 electricity, servo motor to throttle flap down to the "partial load" auxiliary switch II switch point.
The flame, after the formation of LAL terminals 19 electric control device, control two levels of fire or intermediate load. The servo motor in the terminal voltage under 20 through switch S2 and secondary controller open the damper baffle to limit switch III of the switch point. When the auxiliary switch I overrun, the secondary electromagnetic valve is connected. After the burner downtime, LAL control device terminal voltage on the 11 will air door panel down until the limit switch to cut off the IV servo motor power supply. We focus on industrial field accessories and combustion nozzles and other accessories products.
Feedback is very important to us. It is impossible to address issues if we do not know about them!
The item "1055/23 S6 2.4Nm Original New Weishaupt Servo motor Damper actuators For burner" is in sale since Thursday, August 17, 2017. This item is in the category "Business & Industrial\Automation, Motors & Drives\Linear Motion\Linear Actuators". The seller is "burnerworld-2" and is located in , .
This item can be shipped worldwide.
- Brand: Weishaupt
- MPN: Does Not Apply
- Model: 1055/23
- Country/Region of Manufacture: China